Here is the instruction show you guide on how to perform Cartridge lifetime prediction reset for Bendix EC-80 by JPRO Diagnostic Software.This test provides the ability to reset the Cartridge Lifetime Remaining value to 100% after a new air dryer cartridge has been installed.
Noregon JPRO DLA+ 2.0 Adapter
1 Select Cartridge Lifetime Prediction Reset Test and press Enter or the Start Button.
2 The test dialog will be displayed.
NOTE: Reset should only be performed after a new air dryer cartridge has been installed.
3 Click the Reset button to reset the Cartridge Lifetime Remaining value to 100%. The Wetness Level and Total Air Delivered values will also be reset.
4 Selecting Additional Info will display important test and repair information, including explanations for related faults. Click Exit to close this screen.
Cartridge Lifetime Prediction Reset Information:
The CLP Reset should only be performed after a new air dryer cartridge has been installed. Resetting the CLP without changing the cartridge can lead to moisture and water in air system.
Cartridge Lifetime Remaining (SPN 13073) indicates between 100% for a fresh cartridge to 0% for
an expired cartridge. After CLP Reset is performed, Cartridge Lifetime Remaining will read 100%.
For specific instructions, see AD-HFi Service Data Sheet SD-08-12046.
The following faults are the ones related to Cartridge Lifetime Prediction and the actions to take:
Cartridge maintenance prediction pre-worn alert (Flash Code 30-1), SPN 521610, FMI 15:
This indicates the cartridge is approaching its lifetimne limit (15% lifetimne remaining or less).
Cartridge may be replaced and CLP Reset run.
Cartridge maintenance prediction nominal alert (Flash Code 30- 2), SPN 52610, FMI 16:
This indicates the cartridge has reached its lifetime limit or 0% lifetime remaining. Cartridge must be replaced and CLP Reset run.
Cartridge maintenance prediction over-worn alert (Flash Code 30-3), SPN 521610, FMI 0:
This indicates that the cartridge has been in service beyond its service lifetime. This fault also
indicates there may be water in the air system. Check reservoirs for water via drain check valves and service accordingly. Cartridge must be replaced and CLP Reset run.
5 When done, press the Exit button to return to the test selection dialog.
More topics about JPRO Diagnostic,please refer to:JPRO Diagnostics Guide